Enclosed Motor Starter, 18A Contactor, 1ph, remote start terminals, 4X poly, Reset button only, 208VAC coil, O/L 14.5-18A
1) Refer to the motor or equipment nameplate to verify the Full Load Amperage (FLA) at the input voltage. Be sure to confirm whether it is 1phase or 3phase power to the motor. Choose a starter rated for current (Amps) higher than the FLA of your motor.
2) Choose the control power used to close the contactor.
3) Choose the overload by selecting a current range that contains the FLA of the motor from step 1
Once you have done this it should narrow down the starters to only options suitable for your motor and power requirements. Then select your starter based on the following optional criteria:
4) Incoming power
If the line power will be used as the control power as well, this is referred to as a “direct-online starter”.
If the control voltage is not the same as the line voltage we refer to this as “separate control voltage”
If the starter needs to be activated from an external switch, we add terminals to accept the control power input from that switch. We refer to this as “remote start terminals”. It is assumed, in this arrangement that the line voltage and control voltage are the same
If you would like remote start terminals and will be using different voltage for line power and control power, we refer to this as “separate control voltage + remote start terminals”.
5) Buttons on enclosure cover
Reset button only
No cover buttons
We have a variety of educational tools in the NEWS section of our website. For more details on motor starters, you may refer to our detailed guide on selecting a contactor if you want to read up on contactors first. Or if you would like an overview on contactors and overloads and how they work you may refer to our guide on the basics of motor starters.
Springer Controls has a certified UL508A panel shop to build custom starters and control panels up to 500V. For any custom options like HOA (Hand-Off-Auto) starters, pilot lights, control transformers, or volume purchases, please contact us at 904-225-0575
Weight 3.5 lbs AC STARTER FULL LOAD AMPS
AC STARTER CONTROL VOLTAGE
AC STARTER OL CURRENT RANGE
14.5 – 18.0Amps (S)
AC STARTER MOTOR PHASE
AC STARTER COVER CONTROLS
Reset Button Only